Multi fuel flexible liner made from 316L or 904L grade stainless steel. This product carries a Life time manufacturers warranty when installed with Screw-FIX accessories.
150mm (6 inch) 316L Grade Screw fix flue liner
Stainless Steel Pot Hanging Cowl with Mesh
Increasing SCREW-FIX Adaptor to Black Pipe or Single Wall Flue - Ø 125mm SW to Ø 150mm Flex
Chimney Notice Plate
1000mm Black Flue Pipe
316L or 904L Grade Flue Liner is warranted for the lifetime of the appliance it is connected to. (conditions apply)
A double skinned flexible flue liner suitable for relining within a masonry chimney. Flue liner is suitable for use with burning gas, oil, coal, coke, cured dry logs, cured dry peat.
CONSTRUCTION The flue liner has a smooth inner liner made from 316L grade stainless steel and is 0.12mm thick. The flue liner has a convoluted outer skin made from 316L stainless steel and is 0.12mm thick. The Flue Liner is constructed from a single strip of steel which is bent at 180 degrees and then the seam is folded in four planes to give a quattrolock seal.
APPROVAL Flue Liner is approved and listed by HETAS it is also CE approved
INSTALLATION - CHECK LIST 1.Make sure the liner will go down the chimney (this can be done by pulling down a small section of the diameter liner you will be using) 2.Sweep your chimney. 3.Check you pot is in good condition, if you are NOT using a suspended cowl then remove the pot from the stack.
INSTALLATION Flue Liner should always be fitted from the top. Make sure the arrows are pointing upwards (gas flow). Secure a piece of string (at least the same length as the Flue Liner to the Nose Cone (order separately). Now attach the Nose Cone onto the end of the Flue Liner, again making sure the arrows on the Flue Liner are pointing away from the Nose Cone in a upward direction so when the liner is installed the arrows will be pointing to the top of the chimney Pull the liner down the chimney using the string and at the same time have someone at the top of the chimney feeding the Flue Liner down, once the Flue Liner is fitted remove the Nose Cone.
MAINTENANCE It is recommended that chimneys serving solid fuel appliances be swept and maintained as frequently as necessary but at least once a year.